Re: Adding constant hot at the end of a 3 way switch pair?
Originally Posted by joed
A lighting circuit with only lights can have up 1440 watts with no issues on a 15 amp circuit. That would be real watts not the LED or CFL equivalent watts.
It seemed like a bit much before I actually added it all up and then converted to LED equivalents. Just wanted to make sure it is a sane decision to keep 6 screw in receptacles, 2 ceiling fan/light combos, and 6 canless LEDs all on the same circuit. And future/fool proof for any possible future owners. Sounds like you are saying yes, it is.