|05:21 PM - sktn77a quoted supers05 in post Re: Matching AC size to furnace size
If it's not a high humidity a...
|12:23 PM - supers05 quoted sktn77a in post Re: Matching AC size to furnace size
The furnace is too large for...
|04:02 PM - Retiredchief quoted sktn77a in post Re: Looking to replace furnace and AC
A VS motor is an ECM motor w...
|03:11 PM - sktn77a quoted beenthere in post Re: Increasing Air Flow
^^ What he said. And to elabo...
|05:20 PM - dannieboiz quoted sktn77a in post Re: Help my determine my furnace flow and understand my ductwork
Unless you have an enormous ...
|03:21 PM - sktn77a quoted schreibdave in post Re: Mastic vs tape on duct seams?
I am going to buy one of those F...
|07:51 PM - ChiTownPro quoted sktn77a in post Re: Any leverage and/or recourse here?
Sounds like "XYZ" company di...
|07:39 PM - beenthere quoted sktn77a in post Re: Any leverage and/or recourse here?
And post the name of this co...
|09:05 PM - sktn77a quoted ks-man in post Two HVAC Companies - different diagnoses, don't know who is right
He is well aware of what ha...
|05:32 AM - beenthere quoted sktn77a in post Forced air Heater replacement for 2 1/2 car garage
Why not just use an 80% furn...
|07:35 PM - beenthere quoted sktn77a in post Goodman furnaces
Get it fixed under warranty ...
|07:19 PM - beenthere quoted sktn77a in post fully modulating furnace 1st stage cycle rate
I'm not too familiar with th...
|07:51 PM - sktn77a quoted ddsrph in post Goodman heat pump condensor/air handler match
Does Goodman make a air han...