Showing Friends 1 to 1 of 1
- the Musigician
|06:21 PM - oleguy74 quoted Jim Port in post Re: Need help/suggestions with an outdoor antenna ground
And gnore the code prohibitio...
|08:01 AM - Curmudgeon10 quoted oleguy74 in post Re: Questions about Weight/Load Capacity of 4" Box
the box must be rated for the...
|07:12 AM - ddsrph quoted oleguy74 in post Re: Ground fault breaker problem
is gfi breaker wired correctl...
|02:46 PM - oleguy74 quoted Colbyt in post Re: Should I have AFCI's installed in our panel?
Personal opinion. I would n...
|06:13 PM - benjamincall quoted oleguy74 in post Re: Adding a 200A panel - GEC
is the main disc at the meter...
|05:34 PM - oleguy74 quoted benjamincall in post Re: Adding a 200A panel - GEC
It's actually not a sub. I have 4...
|01:38 AM - Californiadecks quoted oleguy74 in post Re: No earth ground on electrical panel
even without a ground rod,met...
|12:30 AM - Californiadecks quoted oleguy74 in post Re: No earth ground on electrical panel
read 820.33/820.40.of the nec...
|12:13 AM - oleguy74 quoted Californiadecks in post Re: No earth ground on electrical panel
Nope. It needs to be in the ground. ...
|07:48 AM - bob22 quoted oleguy74 in post Re: Found 14/2 on 20amp breaker
unless you want to change the...
|09:14 PM - Know A Little quoted oleguy74 in post Re: Checking the cable for faults
for ocasianal use,price is go...
|03:10 PM - rjniles quoted oleguy74 in post Re: Checking the cable for faults
well a megger will run from 3...
|08:48 PM - firehawkmph quoted oleguy74 in post Re: Removed elect. outlets - Then painted walls - Now paint is on outlet wires!!!
with a little thought you cou...
|01:12 AM - oleguy74 quoted Msradell in post Schedule 40 multiple runs
I'm not sure what you are cal...
|10:55 PM - UnPhased347 quoted oleguy74 in post
|10:35 PM - jbfan quoted oleguy74 in post
|10:32 PM - oleguy74 quoted UnPhased347 in post