|08:45 PM - Speedy Petey quoted brric in post Re: Panel behind Door in Wall
30" working space? Looks ...
|08:30 AM - FrodoOne quoted brric in post Re: How to run under cabinet lighting
1. You have no switches on...
|09:03 AM - TROTZINKA quoted brric in post Re: water bonding with pex
if you try real hard you m...
|06:45 PM - brric quoted mj12 in post Re: Stiff outlet
Talk about call backs. I...
|08:07 PM - TipsyMcStagger quoted brric in post Re: UF in 1" Conduit Question
0.168 is the square inch a...
|12:12 PM - brric quoted mako1 in post Re: kitchen appliances
I believe that's what it i...
|12:01 PM - brric quoted mako1 in post Re: kitchen appliances
Not an electrician but do ...
|11:49 AM - brric quoted Runner81 in post Re: Help with a circuit
Do you connect the grounds to...
|06:19 PM - brric quoted flipflopper in post Re: Best Conduit Size for Ease of Pulling?
I found the solution, I believe....
|02:52 PM - rjniles quoted brric in post Re: Underground Service from Meter Pole to Panel
You need 4 conductors. :vs...
|10:39 AM - brric quoted psgama in post Re: Main breaker to sub panel
Your new panel should be a ...
|09:21 PM - joed quoted brric in post Re: Where does one get breakers for this?
They look like bolt-on bre...
|04:56 PM - brric quoted joed in post Re: Where does one get breakers for this?
Those breakers are stablo...
|05:33 AM - rjniles quoted brric in post Re: Sub panel grounding
Was compliant at the time ...
|06:42 AM - brric quoted j-koepke in post Re: Grounding wire size
I have 2 grounding rods put i...
|06:29 AM - jbfan quoted brric in post Re: Grounding a pull box that does not have ...
Where do you get 1/2 20 bo...
|10:30 PM - brric quoted readar in post Re: NM out of J-box... do I need a runner above?
That's what I thought Clutc...
|10:24 PM - brric quoted Arrow3030 in post Re: Wall Light Boxes
When did he say conduit? It's ...
|10:17 PM - brric quoted readar in post Re: NM out of J-box... do I need a runner above?
Good or no good? Excelle...
|10:09 PM - brric quoted jbfan in post Re: Grounding a pull box that does not have ...
I never gave it a second t...