Soffit Venting for Aluminum Sofits
I have a problem with a very hot attic. I do not have enough roof or sofit venting... I Plan to install some roof vent this weekend.
My house has aluminum sofit vents... However they are the punched type and are spaced out about every 8ft or so... I don't think they provide enough air flow, plus I think they might be plugged with blown in insulation...
I cannot get close enough to the soffit from the attic because there is not enough room... So i do not know how I would clean out any insulation that is down there. How do I add more vents? I figured the best way to clean out the vent would be to take them down from the outside... and while I was at that... I could add some additional vents.
So how to I take those soffits down? Also, without damaging the aluminum facia covering that partially wraps around the edge?
Thanks for any help.
Look up my UserName and for "Posts" that I mention Smart Vent.
It is perfect for under-ventilated Intake Ventilation situations, without having to disturb your soffits at all.
It is a Shingle Over Style Fresh Air Intake Vent, which is tapered and gets installed along the bottom of the roof deck after you remove the old shingles.
Hi, Thanks I have never heard of smart vent Before.
However, at the moment I do not think that will help me much since my roof is fairly new and I do not want to go ripping it up. I will consider it for when I actually tear off the roof.
I need advice on putting in more soffit venting. Should I cut the Aluminum and put up regular sofit vents? should I try to take the sofits apart and put in more punched style vents?
Does anyone one else have any other ideas?
if you have soffits overhangs then cut an opening with a circular saw from end to end about 2" wide or more if you like. Then clad the whole overhang with custom bent aluminum on the fascia and a hidden vent vinyl soffit system. Or you can do aluminum soffit with a vented panel abotu every 5' or so.
Unlike Ed I am not at all a fan of smart vent, nor most intake products on the market. The other thing we have done where there is no overhang to create intake is to create a false fascia and make the whole fascia a continuious intake vent.
|All times are GMT -5. The time now is 12:43 AM.|