Poor Attic Ventilation - Roofing/Siding - DIY Home Improvement | DIYChatroom

 DIY Chatroom Home Improvement Forum Poor Attic Ventilation
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

10-23-2008, 09:05 PM   #16
Member

Join Date: Jan 2007
Posts: 2,384
Rewards Points: 1,000

Divide the CFM by 300 to come up with the Square Feet of NFVA required and then multiply the Square Feet x 144 Square Inches to get the necessary NFVA in square inches that you need for Intake Ventilation for the Exhaust Fan.

It is on the www.AirVent.com website, under the brochure about Hip Roofs and how to calculate venting for difficult to ventilate structures if I remember correctly.

Here is the link to the brochure:

http://www.airvent.com/pdf/literatur...s_HipRoofs.pdf

Ed

Here is the pertinent information for the calculation for you.

How Much Intake is
Needed with a Power
Attic Ventilator?

Use the following formula to determine the amount of
intake venting required with a power attic ventilator:

CFM rating of the power attic ventilator 300 = square
feet of intake ventilation needed

For example, 700 (CFM) 300 = 2.3 square feet of
intake ventilation required. (Note: Dividing by 300 is a
predetermined calculation established by the
Home Ventilating Institute.)

To turn that number into square inches, which is the
common method of specifying net free area, multiply
it by 144 (there are 144 square inches in a square foot).

For example: 2.3 (square feet) x 144 = 331 square inches
of net free intake area.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post seppainter Roofing/Siding 20 08-20-2008 08:08 PM klbf Roofing/Siding 2 08-14-2008 08:10 AM mattiasc Building & Construction 5 01-29-2008 07:07 PM kourso HVAC 1 07-11-2007 08:26 PM pramos67 Roofing/Siding 6 03-30-2007 12:27 PM

Top of Page | View New Posts