Unvented water systems
have had an unvented water system installed, do we need a special type of water cylinder as our plumber has used our existing copper cylinder please advise very worried...
Not completely familiar with the vented systems expect from this form. I do understand your concern. If the original vessel was used and designed for use with an open/vented system and now say you have 40-50 psi in it could be a major safety issue. Not knowing if your plumber did his research or not, it is very hard to say if it is safe or not. In a unvented system there should be an expansion tank, and a safety relief valve. Also the tank would need to be rated for the pressure. Copper tanks can be rated to handle this but that doesn't mean you tank can. Look on you tank to see if you can find a rating or manufacture tag. If you just find a manufacture tag with a model number or something try and contact them. I guess do a little homework to try and see if it is able to handle it. I don't know what leval of water presser you have, I was referring to the 40-50 psi as that is common in my area.
some info on vented and non vented
|All times are GMT -5. The time now is 07:16 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.