Replacing Lead Sleeve Soil Stack
Joe homeowner here in dire need of assistance.
I am installing a tile floor in a small 1/2 bath after removing the old vinyl so the old flange/soil stack is not at proper height for the new floor. The house was built in 1921. To my confusion I came across a lead sleeve peened over a brass ring, which I did not encounter in my preparatory readings.
The sleeve was crooked not looking so hot so I thought I should replace it - big mistake. The ACE hardware guy (who are normally spot on) suggested I can essentially wrestle this 4"x7" lead sleeve out of the cast iron pipe and place a new one as the cast iron stack is very difficult to access (therefore cutting and replacing with PVC would be a huge undertaking).
So I proceeded to demolish the sleeve in true boob fashion including 2 full length vertical incisions through the sleeve with my sawzall thinking I could peel it out.
Obviously, I have no clue and it hasnt budged. I could probably use even more force but a crowbar and hammer has not revealed any seams I could exploit for separating the sleeve and at this point I do not want to cause more damage. I have not tired heating the sleeve as I am a bit wary of starting a fire and more frustratingly my handheld benzomatic propane torch does not stay lit well when upside down.
Now I am stuck with a non-functioning 4"x7" battered lead sleeve which I probably should have smiled at and left alone in the first place.
Can I actually remove the sleeve without tearing up the subfloor (the new floor is thankfully not installed yet) or
Is there a way to insert a 3" lead sleeve or PVC sleeve or something inside the remnants of that poor old lead sleeve to bypass this mess and install a new flange to mate with the commode (and walk away quietly)? The toilet horn has a 3" OD.
All help is greatly appreciated.
Thanks in advance!!!
What you should have done is cut it even with the floor with an ossilating saw and used a new PVC flage that has a rubber seal on the outside of it and it just slips inside of the old cast pipe.
I did the exact same thing as you did on the first one I ran across and waisted an hour fighting with it the next one took me about 2 min.
Look at the push tite style.
|All times are GMT -5. The time now is 08:38 AM.|