PVC to PEX connection?
What is the best method to connect 1/2" PVC shedule 40 to 1/2" PEX?
My first thoughts are:
PVC female adapter to PEX male thread/barb fitting
PVC male adapter to PEX female thread/ barb fitting.
Is one better than the other or is there a better way?
Either way would work fine. Personally, I'd opt for the female PVC and the male hose barb PEX fitting. Haven't seen a female thread/PEX barb fitting but they probably do make it.
Not sure what type of pex you are using, but all of our IPS adapters are brass, and threading a male brass (or any metal) into a plastic female fitting is a big no-no, I believe even the codebook (UPC) states this, or has in the past anyway.... I wouldn't do it even if it was code approved. Always male plastic into female brass (or other metal).
We use the wirsbo/uponor style of pex, and they do make brass female adapters. Not sure how readily available they are to public, but..... they are out there.
edit : here are the style we use, and IPS adapters are only available in brass.
I didn't realize that. I'll have to do some reading to see if it is still prohibited. Sorry for the bad info.
|All times are GMT -5. The time now is 10:02 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.