Pumping Rain Rain Water Needs To Be Taken Out Of Home Sewers - Gravity Problem - Plumbing - DIY Home Improvement | DIYChatroom

 DIY Chatroom Home Improvement Forum Pumping rain Rain water needs to be taken out of Home Sewers - Gravity problem
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

06-27-2010, 08:03 PM   #1
Newbie

Join Date: Jun 2010
Posts: 1
Rewards Points: 10

## Pumping rain Rain water needs to be taken out of Home Sewers - Gravity problem

Can an outdoor sump pump safely handle the rain water off of the back of my jhouse (about 15 squares), my patio water (20 X 30 space concrete, and a sump pump from my basement that pumps currently into my sewers but needs to be rerouted to this same outdoor source? In other words, how much water is too much water for an outdoor sump? Also, any info on a back-up generator for this outdoor pump?

Thanks.

John

06-28-2010, 10:53 AM   #2
Member

Join Date: Nov 2007
Location: Nashua, NH, USA
Posts: 7,966
Rewards Points: 1,538

Check the gallons per minute or other volume rating of your sump pump.

If the pump cannot handle the volume, you can install a second pump next to it. (You may need a second pit connected to the first if the second pump won't fit.)

__________________
The good conscientious technician or serviceperson will carry extra oils and lubricants in case the new pump did not come with oil or the oil was accidentally spilled, so the service call can be completed without an extra visit.

 06-28-2010, 02:36 PM #3 Member   Join Date: May 2010 Location: Massachusetts Posts: 133 Rewards Points: 75 You need to find out what the capacity of the pump is in gallons per minute, and also figure out the square footage of the space you are trying to drain. For example, if you have 1000 square feet of surface area, a good rule of thumb is 1 gpm for every 24 square feet of surface area for a worst case 4" per hour storm will give you the gpm requirement. So, for 1000 square feet divided by 24 = 41.6 GPM pump. Then you need to figure the friction and elevation losses, so if your rising 10 feet off the pump before the water spills to gravity you need to factor in a 10 foot head loss when selecting a pump which will effect the gpm rating.

 Tags outdoor sumps capacity

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post DJfixer Plumbing 2 01-01-2009 08:09 AM Bpreuett Plumbing 4 11-06-2007 02:06 PM rgmetro Plumbing 6 04-09-2007 03:57 PM harleysilo Plumbing 2 02-06-2007 03:28 PM june03 Building & Construction 2 10-31-2006 07:24 AM

Top of Page | View New Posts