I have an LP gas fired boiler, all copper piping, all base board heat.
Four zone control valves with four separate t-stats.
My question is how do I find a pressure leak in the system.
The leak is so slight that it may take weeks or months for the pressure
to drop below the cold pressure limit. But then I have to add water to bring
pressure up again. Needless to say, I have learned over the years how
to drain and re-set the expansion tank. The loss of pressure only
occurs when the boiler is running frequently due to extreme cold weather.
It's a nuisance and also bad for the system to keep adding new water.
So do I need to pressurize the system with air to somehow find the leak?
just found that this has been asked on hvac thread
|All times are GMT -5. The time now is 03:05 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2017 DragonByte Technologies Ltd.