plumbing problems newbie needs help ?
our house has a well, the jet pump motor is a 1 hp G.E about 9or 10 yrs old & yesturday it stoped running. it will humm but it wont kick on , my husband filed down the points but that did`nt help we have the pump off right now trying to figure out whats wrong with it any help would be greatly appreciated or amay be a web page that can guide us though figuring out whats wrong , thanks very much:eek:
If the "hum" is the pump running but not pumping water, then it could be:
-a worn out impeller [replacable, but no snap job]
- no water for it to pull [water level dropped, or simply lost it's prime]
- air getting into intake pipe [broken, loose, cracked, or damaged pipe]
If the "hum" is the motor trying to turn but seized up, then it's probably the bearings. In which case, well...
On a ten year old pump, my advice is to go buy a new one and replace the whole thing while you've got it all apart. run you two or three hundred bucks I'd guess.
Does this type of motor have a capacitor? If so, shouldn't it ( they if two) be checked? Just throwing something out there, not sure if this type motor needs the extra boost.
|All times are GMT -5. The time now is 05:15 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.