Please check plumbing for basement bath (pics)
Just finished this up tonight..the guy at the home depot told me to buy this T for the 2" vanity drain line coming up out the ground so I can extend a 4 foot line with a vent. Is this ok to to do right in the wall?
Overall view from main cold/hot copper lines to sharkbite straight connector for hot and T connector for cold (line to vanity and toilet). The wall behind where the toilet is going is the outside wall. Should I have any concern about the sharkbites feezing and failing/leaking?
Vanity cold/hot lines and Toilet line.
Please let me know if you guys think this looks ok. I was really thinking maybe I should of done the copper connection/crimp instead of the fittings..thoughts?
Typically you dont want to run plumbing in exterior walls.
Should I put insulation on the lines? (that foam type that covers copper lines?)
I see what look like a Studor vent--Why don't you just hook the vent up to the toilets vent?
Those cheater vents should not be buried inside of the wall.
|All times are GMT -5. The time now is 11:56 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.