Gas Line Size - Plumbing - DIY Home Improvement | DIYChatroom

 DIY Chatroom Home Improvement Forum Gas line size
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

04-29-2008, 09:12 PM   #1
Member

Join Date: Jul 2006
Posts: 729
Rewards Points: 500

## Gas line size

Hi everyone,

I have a 1 1/4 gas line that tees to 1/2 for water heater, than tees to 1 inc for boiler. I need to tie into the 1 1/4 for gas dryer. Is 1/2 inc good for gas dryer, or should I go with 1 inc? Also, a stupid question, was gavalnized piping allowed for gas lines back in the days? The reason I asked, I just discovered some gavalnized gas line pipe that the idiots that installed it paint it black, thinking it wasn't going to be discovered. I notice when I was taking the pipes apart, and I removed it all.
Thanks

Last edited by helpless handyman; 04-29-2008 at 09:19 PM.

04-29-2008, 11:25 PM   #2
Registered User

Join Date: Apr 2008
Posts: 6,520
Rewards Points: 2,000

You have to size each run of pipe to each appliance, but the sizing is based on the entire system.

I need the following information in order to tell you what you need to know...

Measure the total length of your gasline from where it comes out of the meter all the way to the longest run (farthest appliance from the meter). Diameter of the pipes in this run don't matter. This total length measurement is used to size every single piece of pipe in the system, no matter how long or short it is.

It would also be nice to know the exact btu/h input rating of the gas dryer. I'd guess 35,000...But that is a guess.

I'm also assuming you're on a 1/2 psi system and not a 2 psi regulated system (less common). If all you have is pipe in the house, we'll assume 1/2 psi. If you have a regulator or regulators in the house, we'll assume you're on a 2 psi system.

The safe answer to your question is use 3/4" pipe. 1" would likely be ridiculous overkill. You'd have to bust 150' of total system length or 84,000 btu/h's to push its limits. 1/2" is more than likely good...It'll do 40,000 btu/h's out to 150' of total system length. If you want, give me the lengths and I'll size it for you.

To my knowledge, galvanized pipe has never been ok for gas piping.

 04-29-2008, 11:30 PM #3 Member   Join Date: Apr 2007 Posts: 558 Rewards Points: 500 Don't you need a gas-fitters license?
 04-30-2008, 09:18 AM #4 Member   Join Date: Jul 2006 Posts: 729 Rewards Points: 500 Thanks so much thekctermite Here is some info, no regulators in the house. Pipe runs 36 ft from meter,(1 inc pipe) I am correcting a few things, 1/2 feeds water heater GE 50 gallon. 3/4 inc is feeding 117,000 btu boiler, and 3/4 inc feeds gas stove on upper floor, all coming off the 1 inc main line. I just check the specs and couldn't find the btu's on the manual. I am not at the house, so I can't check the dryer itself. I'm sure there is a metal tag with this info, according to Maytag 1/2 IPS is recommended. It's a Maytag Epicz MGD600T. Hope this helps, I am thinking the 1/2 should be good? Let me know what you think, Thanks! Last edited by helpless handyman; 04-30-2008 at 10:18 PM.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post Doug Crf General DIY Discussions 20 02-26-2011 12:29 AM schott HVAC 17 06-02-2008 04:16 PM brownie47854 Electrical 14 04-22-2007 01:50 PM travishume Plumbing 23 09-26-2006 08:51 AM skellies Plumbing 3 06-18-2006 09:19 PM

Top of Page | View New Posts