Originally Posted by Javiles
What aim quoting is under the IPC
1 hard to tell is that a wye at the stack and sink waste arm.? If it is must be a sanitary tee not a wye.
2 waste arm to sink 5 feet from stack in 1 ½ pipe 2” 8 feet.
3 how are you picking up the toilet? Within 5 feet of the vent
4 clean out at the base of the stack. As someone mentioned.
Thanks for the follow up....
1) Yes it is a sanitary tee. Made sure of it when I bought it.
2) thanks, my 1 1/2 waste arm should not be more than 4 feet, so I should be good.
3. The toilet is just roughed in where it is in the picture. I am not sure there is a vent for the toilet. I just have the 4 inch pipe sticking out of the concrete in which I just placed a flange for the picture. that is one of my main concerns. I am assuming that the toilet and 3" drain both route back to the backwater valve and then to my house main stack drain that sits just in back of this picture about 4 feet.
4) clean out bought this afternoon