central heating boiler leacking from relieve valve
I have a Alpha SY24 wich was leacking from the relieve valve.
But every time I was filling the system at cold to 1bar, as soon the water was getting hot the pressure build up to 2.5bar
At some stages the system was loosing its pressure from the relieve valve to 0bar, so I thought to replace the releieve valve to solve the problem.
But it keeps doing the same thing with the new valve.
Is the expantion vessel the problem.
is it possible the fill valve is not shutting all the way?
check the expansion tank ,if all hot then water log .pressure in tank should be 12psi .drain the tank. that should do it
The filling loop is removed every time I fill the system.
I will chek the expantion vessel pressure
Thanks to all
|All times are GMT -5. The time now is 11:24 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.