California plumbing code on grease trap?
I am trying to find the latest california plumbing code especially the appendix H to properly sized a grease trap. If anyone have access can you post it here?
This is what I found on the web but not sure if it's the latest?
(# meals/peak.hr)*(flowrate)*(retentionrate)*(storagefactor )=grease trap size.
Where as # meals/peak.hr = # seat * meal factor
a. fast food = 1.33
b. restaurant = 1.0
a. with dishwasher = 6
b. with out dishwasher = 5
c. single service = 2
Retention time =
a. Commercial kitchen w/ dishwasher = 2.5
b. Single service kitchen = 1.5
Storage factor =
a. 8 hrs = 1.0
b. 12 hrs = 1.5
c. 16 hrs = 2
d. single service = 1.5
Umless someone on here knows the codes there, then your in luck, for now, your best option is find someone locally for help.
For a quick response contact a manufacture of a grease interceptor, they are generally in current compliance with all model codes.
These Grease Interceptors I have seen work wonderfuly.
|All times are GMT -5. The time now is 05:10 PM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved