Originally Posted by FreshMeats
Couple questions I have:
1) Is there anythign that says I can't exit my plumbing through the side of my vanity?
2) Can I use a paired wye and elbow to make the corner (i fogot to label it on the attached sketch).
3) If the above is acceptable can I just cap the end or do I need to have a cleanout and then have access to it?
4) Can the two different santees be stacked on top of each other?
1---hole in vanity is fine
2---no need for that Y with the cap---just use a 90--a long sweep would be good if it will fit.
3---No cleanout needed
4---Yes on the sanitary tees.
If the arm from the vent to the vanity with the hole in the side is more than 5 feet--add a vent.