2nd story bathroom, drain &vent, please help!!!
I am adding a second story bathroom on top of the 1st story bathroom.
1st story bathroom has a 3" drain under the slab, for the toilet, toilet is vented thru 2" pipe and sink discharges into this vent. So it looks like this:
I ---U lv
=== is a 3" pipe, --- is 2" pipe, I is a 2" vent and U is a water trap,
I plan to cut the 3x3x2 tee out, replace it with 3x3x3 tee and run a 3" stack up to the second story, so i can drain a toilet down. The sink and a toilet will be along the same wall and a shower 8' away.
I was hoping to make it simple, run this 3 inch stack to the 2nd floor, it would change to 2" at the tee between the joists and 2" will serve as a vent for both 1st and 2nd floor toilets.
I am not sure if I can drain my sinks and shower into the same stack. and also if i need any extra vents. The way i drew it, that 2nd story shower and a sink will have a separate vent and will drain below 2nd story toilet. Should I extend this 2" stack all the way down and try to drain it into horizontal 3" pipe before the 1st floor toilet vent? I am looking for the simplest solution, horizontal pipe is under the slab and I want to avoid a lot of concrete braking
I would highly appreciate an advice from the professional. Our project is way over budget and we cant afford a licensed plumber to do the work. I pulled a building permit and it means the plumbing will have to pass an inspection.
Thank you very much for your input!
Here is a better diagram, so you guys can see what i am up to.
Please, let me know if it meets the code and if it will work without any issues.
Thanks a lot!
No it will not meet code. You are creating a wet vent for the first floor drains.( Drain water from the second floor is flowing past the first floor vents.) Run the new 3 inch line from the second floor drain back to the 3 inch main drain (horizontal pipe). Tie in the second floor vent into the 3 inch going thru the roof.
Not sure your existing first floor arrangement meets code either, but it existing.
ok ,so i guess i have to preserve a separate vent for the 1st floor toilet and sink, right?
I updated a diagram, also, what fittings should I use?
The whole horizontal 3" pipe is under the slab, and that new vent would have to be under the slab too and have a small horizontal section till it meets the wall. How can I add a horizontal 2" vent to the horizontal 3" drain?
Also, is it OK to have a shower trap 8' away from the vent?
|All times are GMT -5. The time now is 05:22 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.