This is my design for a GFCI Tester to check the current leakage margin to help analyze nuisance trips.
The box is a Carlon Handy Box
S1 is a C&K miniature Toggle model E107 which is center OFF and momentary in the spring loaded up or down position.
DS1 is a green neon which pulls 1.3 mA. Any color neon can be used but there is variance among colors and models. I tuned my Neon circuit with a bleeder resistor to pull a measured 2.01mA @ 119.5V.
|All times are GMT -5. The time now is 09:14 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.