Variation In No Load Amperage Of Similar Rated 3- Phase Motors - Appliances - Page 2 - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Variation in no load amperage of similar rated 3- phase motors
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

11-13-2011, 03:09 PM   #16
Newbie

Join Date: Nov 2011
Posts: 9
Rewards Points: 10

Quote:
 Originally Posted by Master of Cold Is there a y-delta starter ?
Quote:
 Originally Posted by Jackofall1 I have to ask, when you serviced the fan you took the sheaves off both the fan and the motor, are you certain that you put them back on correctly. If you didn't this would explain the high current draw under load, you have sped the fan up resulting in moving more air, just an idea. As for testing the motors, measure the resistance of the field windings, each set of windings should be close to each other and have low ohms readings. I would select the motor with the most consistant low readings field windings to field windings. An excerp from a motor testing article http://www.gainesvilleindustrialelectric.blogspot.com/ "To test the windings, use an ohmeter. Make sure any jumpers for voltage selection remain connected. For a nine lead, dual voltage motor connected for 480 volts, these would typically be the 4-7, 5-8, and 6-9 connections. Measure the resistance from 1-2, 2-3, and 3-1. The resistance readings should be between 1-2% of each other - in other words, BALANCED! There is no way to tell how much resistance you should get, but it is typically low. Realize that you are testing with a DC battery. Therefore, you are reading the resistance of the copper wire. In many cases, this will look like a short circuit. GOOD! It's when it doesn't look like a short circuit that you have problems. As long as the readings are low and balanced, you're ready to go to the next step. I can't tell you how many motors are brought to us because "the windings are shorted." Don't make that mistake." Unless you have a megger you will not be able to test the insulation quality of the motors. Mark

Thanks your response Mark. We did not touch the blower at first. The initial motor failure was on low insulation. Then we fitted a spare motor with 2 amps no-load amperage & noted that it was drawing 40 amps & overheating / tripping. later we fitted another reconditioned motor of 2 amps no-load amperage & again same drew 37 amps on load & getting heated. We then checked the blower & connecting v-belt & found all in order. hence we suspect motors primarily or it might be the blower as well when running at the high rpm, although no tell tale evidence of same. We have the ohmeter & megger & will check as suggested.

Also the motor that was showing low rinsulation was sent to an electrical workshop for repairs & after coming back, same was checked & found to be drawing 14 amps on no load. Could u suggest some light on this high no-load current. thanks your assistance. Brgds / valentine.

11-13-2011, 03:22 PM   #17
Experienced

Join Date: Dec 2010
Location: Southern Michigan
Posts: 2,822
Rewards Points: 2,000

Quote:
 Originally Posted by valentine Thanks your response Mark. We did not touch the blower at first. The initial motor failure was on low insulation. Then we fitted a spare motor with 2 amps no-load amperage & noted that it was drawing 40 amps & overheating / tripping. later we fitted another reconditioned motor of 2 amps no-load amperage & again same drew 37 amps on load & getting heated. We then checked the blower & connecting v-belt & found all in order. hence we suspect motors primarily or it might be the blower as well when running at the high rpm, although no tell tale evidence of same. We have the ohmeter & megger & will check as suggested. Also the motor that was showing low rinsulation was sent to an electrical workshop for repairs & after coming back, same was checked & found to be drawing 14 amps on no load. Could u suggest some light on this high no-load current. thanks your assistance. Brgds / valentine.
A new 20 hp 3 phase 480 volt motor should pull about 10 amps, so 14 amps no load is close.

http://www.baldor.com/products/perfd...ing=40CMB-CONT

Hook it up, if its still pulling high amps (37 amps) your load is too great for the motor.

Mark

__________________
When its all said and done there is usually more said than done

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post 1488rob Electrical 36 01-28-2014 04:44 PM qtipextra Electrical 9 11-07-2010 10:01 PM meglomachinist Electrical 19 09-10-2009 03:46 PM Roy Rowlett Electrical 21 08-20-2009 06:55 PM crazydog Electrical 10 08-20-2007 10:47 PM

Top of Page | View New Posts