- - goodman furnace
||01-26-2013 11:48 AM
I have a goodman furnace that the induce fan runs but it would not ignite, i replaced the electronic ignighter
||01-26-2013 02:06 PM
Sounds like the pressure switch is not closing. Pull the vacume tube and clean it out. Also check to see that both ports where the hose hooks to are clear. Also, check the intake and exaust lines to be sure there is no obstructions.
|All times are GMT -5. The time now is 02:08 PM.
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved