Replace 2x12 With Double 2x6?? - Building & Construction - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum replace 2x12 with double 2x6??
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

06-04-2011, 09:01 AM   #1
Newbie

Join Date: Jun 2011
Posts: 1
Rewards Points: 10

## replace 2x12 with double 2x6??

I have 2x12 floor joists under a second floor bathroom. They are 16" OC and span only 8'0". I would like to replace 1 of these with a double 2x6 to make some plumbing easier.

Is there any problem with this?

06-04-2011, 01:33 PM   #2
Residential Designer

Join Date: Sep 2010
Location: Orange County CA.
Posts: 1,386
Rewards Points: 688

Maybe, maybe not.

My guess is ...........

.........probably yes, it is a problem.

Andy.

 06-04-2011, 02:03 PM #3 Civil Engineer   Join Date: Mar 2009 Location: Boston Posts: 5,679 Rewards Points: 4,938 A nominal 2x12 with true dimensions of 1.5" x 11.25" has a moment of inertia of 178 in^4. A pair of nominal 2x6 with true dimensions 1.5" x 5.25" has a moment of inertia of 36 in^4. This makes the 2x12 about five times as strong in bending as the pair of 2x6's. Whether this is a problem in your particular case depends on the loads, the span, and the connection geometry.

 06-04-2011, 05:38 PM #4 Member   Join Date: Mar 2011 Location: northwest indiana Posts: 40 Rewards Points: 25 i also see it as a problem , the 2x12 was put there for a reason
06-04-2011, 06:27 PM   #5
Framing Contractor

Join Date: Feb 2009
Location: NE Ohio
Posts: 1,214
Rewards Points: 126

Quote:
 Originally Posted by fulton 22175 i also see it as a problem , the 2x12 was put there for a reason
Not necessarily. When a floor is figured, it is figured for the longest span. All the joists generally are the same width, so this results in some joists that are way oversized. I would say to check and make sure that the span is indeed 8'. Just because a joist runs over a wall, doesn't mean that wall is a bearing wall.

 06-04-2011, 06:44 PM #6 timthetoolman   Join Date: Oct 2007 Location: Milwaukee Posts: 58 Rewards Points: 75 oh ohhh! Does someone need a soffit somewhere? Run it under the joists with a soffit.?. If you make it a little wider than the tub, this usually looks really good below. I like the sounds of 2X12 joists only spanning 8 feet, overbuilt how I like em. But don't mess with cutting apart your joists man...never a good idea. Last edited by timthetoolman; 06-04-2011 at 06:46 PM.
06-04-2011, 07:19 PM   #7
Member

Join Date: Jan 2011
Posts: 56
Rewards Points: 75

Its pretty unlikely theres bearing walls only 8 ft apart. You can drill holes in joist you know. How big of holes do you need? People always want to move structural elements to make plumbing easier, even on the contracting side of building. Theres a reason we frame them before the plumbing is ran. Be carefull when messing with structural elements.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post WillK Building & Construction 6 03-09-2011 08:55 PM plichtenstein HVAC 5 08-24-2010 02:41 PM peyton HVAC 8 04-19-2010 10:02 AM Jeremy Hillary Boob, PhD Plumbing 3 04-03-2009 08:39 AM shadowx360 Electrical 2 07-09-2008 02:44 PM

Top of Page | View New Posts