||Thread Tools||Display Modes|
|08-12-2010, 02:11 AM||#1|
Join Date: Aug 2010
Posts: 2Rewards Points: 10
Insulating & Ventilating Vaulted Ceiling
The family room in our home has vaulted ceilings and gets very hot on a warm day to the point the A/C cant keep the room cool. The current construction of the roof & insulation ceiling is:
The roof is dark composition shingle, over ½ CDX ply wood. The framing is 2x10 rafters 24 OC. And the room is finished in sheetrock. Each rafter bay is stuffed with fiberglass insulation. 3 small ventilation holes are drilled at the end of each rafter bay. The rafter bay cavity is 9" high. Ventilation is minimal.
While we have R30 insulation the room still gets unbearably hot. Our guess is the lack of ventilation allows heat to build up and ultimately overwhelms the insulation.
We are looking at removing the roofing and CDX sheating to re-insulate with POLY ISO boards and increasing ventilation. We have 3 different options and trying to find the best approach for minimizing thermal gain in our home. We live in central East SF Bay Area. Summers are dry and can get very warm - 100+ degree days not uncommon.
In each option we increase ventilation in each rafter bay.
Option 1 - Use 2 sheets of 3 PolyISO, providing R36. Create a 3 venting space between the insulation and the top of the cavity (9" Cavity - 6" Insulation).
Option 2 - In this option we increase the insulation by 1.5 getting to 7.5" total insulation increasing the RValue to about R45 - Create a 1.5 venting space between the insulation and the top of the cavity
Option 3 - In this option use two 3" PolyISO sheets - but we Increase ventilation flow around insulation boards by putting 1 furring strips between each 3 sheet of PolyISO. Our goal is to increase airflow between PolyISO sheets to reduce the overall temperature in rafter cavity. Net result is 1" of airflow between boards, 2" between insulation and top of the cavity.
Would appreciate input on best approach to reduce thermal gain.
Thanks in advance for your help Frank
|08-12-2010, 10:14 AM||#2|
Ole Wood Worker
Join Date: Sep 2008
Location: Chattanooga, Tennessee
Posts: 10,299Rewards Points: 186
Blog Entries: 1
You didn't say but I assume you have a good ridge vent. There should have been the styrofoam chases against the underside of the decking to get a good air flow also.
This may not interest you but when I built my house with a vault, I had the same problem, I looked into installing a "skin roof". A skin roof is a roof built above your existing roof with an air passage between. The skin roof is built with the chimney effect in mind.
Hot air rises drawing in cool air at the bottom and discharging at the top. This would keep the existing roof much cooler in another way, the sun would not hit the existing roof. I don't know if this would work or not as I have never seen one personally, maybe someone on the forum has. Just a thought.
New members: Please consider adding your location to your profile.
If you do what you've always done, you'll get what you've always got.
|08-12-2010, 03:51 PM||#3|
Join Date: Mar 2009
Posts: 11,575Rewards Points: 5,216
I believe R-30 is 9-1/2", R-25 is 8", are you positive on your R-values for the inch thickness?
22-1/2" rafter blocks with only 3- 1-3/4" holes (older) have a sq.in.NFVA of 7.22, less than 1/2 of the required 18 NFVA.
Read these: http://danperkinsroof.com/1108_JCL_Perkins_A.pdf
http://www.buildingscience.com/docum...aspen-profile/ Click on all the links.
Be safe, Gary
If any ads are present below my answer or words underlined/colored, I do not condone/support/use the product or services listed/linked to, they are there without my consent.
17,000 dryer fires a year, when did you last clean the inside of the dryer near motor or the exhaust ducting?
|Thread||Thread Starter||Forum||Replies||Last Post|
|HELP! lighting question for vaulted ceiling||pauls||General DIY Discussions||5||07-03-2010 05:53 PM|
|Insulating a Perfectly Good Ceiling||Creekbender||Building & Construction||2||03-02-2010 07:55 AM|
|Insulating Vaulted Ceiling||cibula11||Building & Construction||11||01-31-2010 09:48 AM|
|Insulating basement ceiling - your recommendations?||jtmann||HVAC||8||11-24-2009 05:44 PM|
|insulating vaulted ceiling||johnnyboy||Building & Construction||7||08-26-2009 11:55 PM|