Hired licensed contractor past electrical inspection but incomplete
He finished couple months ago with addition. Want to install electric wall oven. Called for estimates and realized after seeing several Electrician that wiring wasn't inspected up to code and improperly done. What should we do? Permit for electrical don't think we have but check list and initial from inspector states he checked. We looked to see and shows on plan finalized. What should we do?