||Thread Tools||Search this Thread||Display Modes|
|03-08-2007, 12:25 AM||#1|
Lehigh Valley PA
Join Date: Mar 2007
Would this pass inspection?
Okay, need some more help here. I am concerned with the electrical in this house and the way it is distributed...
How many circuits does the typical 3 bedroom, 2 bath, 2 1/2 car garage, ranch, no basement house have?
I have a decent size panel and the sucker is pretty much full. I'm looking to split the bathroom circuits into 2 seperate runs to bring that up to code since they are both on the same circuit now, along with the hallway light and outlet.
I looked at the panel tonight and I'm nervous about having an inspector come and look at it for any work.
Anyway here is a picture of the box with the cover off, let me know what you think?
Some other things that I noted was on the label inside the cover:
"GE Cat No. TX2820E Model 2"
"Use with class Nl, G-E Type TR, TRP, TQL or TQAL breakers"
"DO NOT EXCEED: MAX 1-POLE CKTS in sub section...
10 - with 50A sub main disconnect, 5 per
12 - with 60A sub main disconnect, 6 per
14 - with 70A sub main disconnect, 7 per"
When I look at the panel it has a 70A disconnect for the sub section but I count 17 circuits there now, due to use of 1/2 height breakers in a lot of the openings.
Each breaker in the picture with a green sticker on is a double-half-height breaker.
I have one open spot and one that feeds 2 utility outlets that I don't need right now that I can remove. Problem is if I'm reading this right that still won't allow me to add my 2 runs for the seperate baths..... correct?
How should I interpret this message on the label?
Other details on the label:
200A 120-240V A-C 3-wire
No greater than 100A per stab
Thanks for any help...
|Thread Tools||Search this Thread|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Electrical issues with home inspection||toolmaan||Electrical||20||08-10-2007 05:52 PM|
|Shimming Trimmers to Pass Framing Inspection?||Ricky D||Building & Construction||6||06-03-2007 09:55 PM|
|Home Inspection||satchmo||General DIY Discussions||5||04-07-2007 12:28 PM|
|Final Inspection requirments||K&G's Cabin||General DIY Discussions||1||01-28-2007 01:44 PM|
|How is electrical inspector doing the inspection...||KUIPORNG||Electrical||2||08-15-2006 08:46 PM|