Would this be in the gray area of the NEC?
Im planning my sub panel install for my garage im bulding. I know I cant run NM-B with Insulation thru conduit. Running conduit all the way from my main breaker box out to the corner where i need to go thru the wall would be tough.
So i was gonna run 6-3 W G NM-B (Romex) out to the corner in the basement and into a juntion box, where the Schd 40 PVC would start, and just strip the insulation of the nm-b and pull the single wires thru the conduit to the sub panel in the garage.
Would this be ok? The single wires within the NM-B cable are THHN, but they dont have the clear plastic covering as well as the outer jacket like true THHN has.
Otherwise, I guess I would have to splice over to single THHN in the junction box, and pull them out to the Sub. I was just trying to make it easier and use the one cable and no splices.
Thanks in advance.....
Last edited by stagger19; 08-15-2006 at 01:01 PM.