||Thread Tools||Search this Thread||Display Modes|
|07-27-2008, 07:21 AM||#31|
It was a dark and stormy
Join Date: Jul 2008
Location: NW of D.C.
Wiring Size Calculations?
It's 6 AM, so I can't guarantee these numbers, but, for a max of 5% voltage drop:
From turbine, going 1000' to invertor, ~#2 AWG. Using #8 will starve the battery charger circuitry and you won't get anywhere near the battery performance you should be getting.
The DC voltage into the invertor is probably below the spec value for this device. I hope it has not been damaged.
From invertor and going 1400' to load, ~#0 AWG.
At this point, I can't see cable heating [due to the current passing through it] as a problem.
Since you're not paying PoCo for kwh, I don't think there is a payback period for the money you spend on this equipment.
You've already bought the batteries so I'd put the next few dollars into the 1000' cable. The first priority is not abusing the equipment.
Or, we put the invertor/batteries next to the turbine and figure out how to ship 2500w over 2400'. Step-up/step-down transformers are starting to look good.
If you can supply me some prices for copper and aluminum cables, we can trade off the money you will spend for the performance you will get, and show this as dollars per watt or dollars per watt-hour.
You're a paying customer, so see if the turbine people will give you whatever technical data, schematics, application notes, everything on the generator that is driven by the turbine.
I'm especially interested in whether it is a DC gen or an AC gen with rectifiers.
And the voltage vs. current curve(s) for this gen would be good.
Last edited by Yoyizit; 07-27-2008 at 06:16 PM. Reason: added copper and aluminum
|Thread Tools||Search this Thread|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Wiring diagram for three-way switches with pilot light||SaxTeacher||Electrical||34||09-15-2013 09:53 AM|
|Size of whole house fan needed||Doug Crf||General Discussion||20||02-26-2011 01:29 AM|
|2x100a sub on service main||jambud||Electrical||17||03-12-2008 11:31 AM|
|Replacing wiring in middle of run, ungrounded lighting circuit||alexz||Electrical||3||07-05-2007 10:53 PM|
|Knob & Tube wiring - How concerned should we be?||hotdiggitydog||Electrical||6||04-11-2006 09:52 PM|