Wiring new Honeywell Relay to Breaker box
Hi all, got a crawl space heater not working that I have narrowed down to an old (25yrs+) R841C1011 heater relay/transformer.Has 3 wires going to breaker box...red,blue,and black. Honeywell replacement/upgrade R841C1169 has 4 wires for box...red,blue,black,and an orange wire. Can't find schematic for 1169.where does orange connect?
It doesn't. Probably for use on 208 Volt systems. Cap it off with a wire-nut and ignore it.
240 Volt incoming line connects to black and blue.
240 Volt outgoing line to heater connects to blue and red.
Thermostat connects to the other 2 small red and white wires.
Thanks KB, I'll give it a try. Box unit came in reads 208/240 V 50/60 HZ and is replacement for 6 other units.
Thanks again for the info.
|All times are GMT -5. The time now is 05:36 AM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved