Originally Posted by scrayzee21
You will need to run 4 wires to the garage, 2 hots, 1 neutral, 1 equipment grounding conductor. You will need to install a GES (grounding electrode system at the garage, this usually just consist of driving two ground rods, your neutral and grounds shall be seperate at the garage panel, You also need a disconnect at the garage, a main breaker panel it usually the easiest. You need to size the wire according to the load of the gargage. What did you plan on using the garage for?