Wiring Gage Questions - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Wiring gage questions
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

03-27-2006, 05:15 PM   #1
Newbie

Join Date: Mar 2006
Posts: 3
Rewards Points: 10

## Wiring gage questions

Wiring gage questions

We are currently digging a trench to have an exterior wire go from the house to a back barn. The distance is about 120 feet and the electric in the barn is going to be use for lighting. Could you please tell me the correct gage and wire type for this project?

03-27-2006, 05:41 PM   #2
Electrical contractor

Join Date: Mar 2006
Posts: 44
Rewards Points: 25

Just Lighting? How much lighting?
Never going to need a drill out there?
And you don't weld or anything?
And won't put a tiny little fridge out there for when you are working on the brakes?

03-27-2006, 05:44 PM   #3
Newbie

Join Date: Mar 2006
Posts: 3
Rewards Points: 10

## wiring gage questions

Is a horse stable, so just horses back there… Perhaps a dozen light bulls all together...

Good point... I used the word barn!

 03-27-2006, 06:17 PM #4 Electrical contractor     Join Date: Mar 2006 Location: Philadelphia area Posts: 44 Rewards Points: 25 Robert Wilber Licensed Philadelphia Electrician Philadelphia License # 3516 - 16765 * I would humbly suggest that you pull a circuit out there for a receptacle too. If you have 12 x 100 watt lamps, then you will be pulling 10 amps on the line. Run a separate circuit for a receptacle as well, and put in a GFI. 120 feet is a 240 foot roundtrip. the formula for wire size is a corollary of the voltage drop formula. Voltage drop =KIL/CSA where K is conductance, I is current, L is circuit length and CSA is cross sectional area in circular mils. so... CSA= KIL/V drop CSA= 11 [K factor of copper] x I [say 12 amps] x 240 feet / 3 volts CSA= 11*12*240/3=10,560 circular mils 10 gauge is 10,380 circular mils. Sounds like a good fit. So, run 240 out on a 10/3 with ground type UF cable out to the stable and put in a 2 circuit loadcenter. Make sure to isolate the neutral from the ground at this panel. According to NEC 250.32 it is not required to have a ground rod at the stable. I think having one might create problem ground currents that could interfere with the horses, but get advice from your local inspector and the authority having jurisdiction. * I haven't done this myself, so I haven't checked my opinion on this with any "Authority Having Jurisdiction" This is my interpretation of what I have read in the 2005 NEC * LIFE SAFETY WARNING! [disclaimer] This information is provided for the use of parties as they see fit! I am not responsible for the application of this information by any party, including those lacking sufficient skill or knowledge to perform these steps safely and any hazard created is the SOLE responsibility of the user.
03-27-2006, 06:23 PM   #5
Newbie

Join Date: Mar 2006
Posts: 3
Rewards Points: 10

## Thank you soooo much!!!

I really appreciate that you took your time to explain why and how you calculated that!!!

Pretty neat and tidy, Thank you so very much

 03-27-2006, 08:37 PM #6 Electrical contractor     Join Date: Mar 2006 Location: Philadelphia area Posts: 44 Rewards Points: 25 welcome
03-27-2006, 09:12 PM   #7
Electrical Contractor

Join Date: Jun 2004
Location: Newnan GA
Posts: 7,027
Rewards Points: 650

Make sure you protect the wiring. I've seen horses chew anything and everything.

__________________
"The problem isn't that Hillary Clinton lies. We all know she lies. The problem is that her supporters don't seem to care"

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post LMH Electrical 2 05-24-2009 03:06 AM alexz Electrical 3 07-05-2007 08:53 PM PAULYBOY Electrical 1 03-28-2007 06:20 PM hotdiggitydog Electrical 6 04-11-2006 07:52 PM eastment Electrical 4 11-26-2005 11:52 AM

Top of Page | View New Posts