I have been reading up on this all over and i have found several different answers, and other posts or other questions that are just confusing me now.
so since my drill battery is charging, i figured i might as well double check with everyone.
i have an out let that is controlled by a switch. the powered wiring goes to the outlet first, than from there a switch is connected. so i know i have to splice into the wiring that is at the outlet. I have attached pics so everyone can see what i am working with. I have not yet dropped any airing for the fan, everything you see is as it stand right now, just pulled the cover off.
now i already have 3 cables coming into the outlet box, but nothing else is switched. my only guess is the power goes from here to the other outlets that are always powered, and this is just the only one on a switch. Is there going to be a problem if i run a 4th cable into here for the fan?
so if its good to just drop another cable into here and go i just want to make sure i have everything in order.
connect all whites with white.
connect all blacks with black
run black wire from bundle to gold side of outlet with a bridge
run white wire from white bundle to silver side with bridge
now where should my white and black wire from the fan connect once its dropped so i can use the switch for the can only?