# of wires in 1 1/2" octagon box
Hi I am new to this forum and also to electrical work but I have read some books including Residential Wiring to the 2008 NEC by Jeff Markell.
I am running (in emt) switched porcelain sockets in parallel. There is also a hot wire passing through to downstream. So each octagon box has a red wire in to pigtail to porcelain fixture, then red wire out to the next box. Also white neutral in, pigtail, out. Black wire in a loop passes through the box. It's 12 gauge wire.
Per sources, I am counting six wires: two red, two white, one black, and the fixture. Pigtails to fixture it seems do not count? Did I count this right? Do those porcelain fixtures get hot at all? I am looking at the actual roughed-in work and it seems like a lot of wires for that box. I will add extension if I have to but would rather not 'cause then the light is a little lower off the ceiling.
If you are in the US...
Count the number of wires entering or leaving the box, not the fixture wires or pigtails. Multiply that number X (2.25). If that number is less than 15.5 (the volume of an 1 1/2" octagon) then you are OK.
Thanks K Buz for your reply.
I ended up putting the extender on. Just seemed to make sense to use caution here, I could envision those boxes getting very crowded. I will not be hitting my head on the light bulb, so I will be ok.
|All times are GMT -5. The time now is 03:25 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.