wire size for sub panel
What size and type of wire would be suitable for powering a 100 amp sub panel from a 200 amp main panel? Distance will be approx 40 ft with feed running through an attic. Location, Cleveland, OH.
Do you need all the 100 amps in the sub? You could feed it with # 6 and use a 60 amp breaker in the main.
#2 al is what I use, and put it on a 90 amp breaker.
|All times are GMT -5. The time now is 08:44 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.