wire size for sub panel
What size and type of wire would be suitable for powering a 100 amp sub panel from a 200 amp main panel? Distance will be approx 40 ft with feed running through an attic. Location, Cleveland, OH.
Do you need all the 100 amps in the sub? You could feed it with # 6 and use a 60 amp breaker in the main.
#2 al is what I use, and put it on a 90 amp breaker.
|All times are GMT -5. The time now is 12:12 PM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved