Wire Size - Electrical - Page 2 - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Wire size
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

03-30-2008, 12:09 PM   #16
Idiot Emeritus

Join Date: Mar 2008
Posts: 1,849
Rewards Points: 1,492

Thanks, Marc. I'll write that down as a reference. Very handy when working with metric equipment.

In the above example, a 5.4 anp motor about 600' away, #8's would be my choice as well.

Rob

03-30-2008, 01:13 PM   #17
Member

Join Date: Jan 2008
Location: Oregon
Posts: 116
Rewards Points: 75

Quote:
 Originally Posted by idoelectric #6 copper stranded is good for 30 amps at 120v for a distance of 500 ft. I'm not sure where the 7 amps came from? Cmils= 2 x K x I x D / VD
I believe you're mistaken. Use the formula you posted and see what you come up with. Unless you're shooting for 15% VD?

FYI, the 7 amps was calculated using this formula:

I=(CM x VD)/(2 x K x D)

03-30-2008, 03:45 PM   #18
Member

Join Date: Feb 2008
Location: Atlanta, Ga/Hamilton, Al
Posts: 2,487
Rewards Points: 2,350

Quote:
 Originally Posted by elkangorito I don't know about the USA but calculating the voltage drop for a given cable length & current, is not a simple process in Australia.
I generally use the formula VD = (2KxIxD)/cm

where K is a typical value for the resistivity of copper, 12.9 ohms/cm-ft
I is the current
D is the distance, in feet
and cm is the circular mils of the wire.

I transpose the equation into cm = (2KxIxD)/VD

where VD is 3.6V for 120 V or 7.2 for 240 V.

So if I know the current, this tells me the wire size in circular mills. I can then select from a chart of standard gauges to the nearest size.

Our wire ampacities are selected from a table of based on what conditions the wire is used in. Most typically, it is based on no more than 3 conductors in a conduit of cable, or directly buried in earth. There are other tables for free air and other conditions.

InPhase277

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post stan 41943 Electrical 19 03-06-2008 02:29 PM Skydmark1 Electrical 12 12-15-2007 05:00 PM fburke Electrical 4 07-28-2007 09:29 AM mwtuck HVAC 2 12-01-2006 05:06 PM lochcarron Electrical 1 04-10-2005 07:43 PM

Top of Page | View New Posts