DIY Chatroom Home Improvement Forum
05-05-2011 11:40 AM
I have a 0.9 amp 220V motor which I need an outlet box.
What size wire and circuit breaker do I need to run 30 feet of wire?
05-05-2011 01:01 PM
14/2 and a 15 amp breaker
All times are GMT -5. The time now is