Wire Gauge VS Length - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Wire gauge VS length
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

03-26-2008, 04:54 PM   #1
Member

Join Date: Jul 2007
Posts: 308
Rewards Points: 250

## Wire gauge VS length

Hi;
I am going to run several circuits up to my attic, then back down walls upstairs to receptacles.
I don't think any run will be more than 50ft. I am trying to find a rating vs length chart.
This is standard NMB #12 cable that will be fed by 20A breakers.

Thanks

FW

03-26-2008, 06:45 PM   #2
Idiot Emeritus

Join Date: Mar 2008
Posts: 1,849
Rewards Points: 1,492

Amp rating vs. length doesn't matter as much as voltage drop vs. length.

If you wanted to, you could use a 20 amp breaker on #12's 10,000 feet long. Of course, if you had any kind of load on it, there would be very little voltage left to feed the load. The resistance of #12 copper is 1.619 ohms per 1000 feet. It doesn't matter if its NM, THHN, an extension cord, or whatever.

Suppose you needed some light in a chicken coop a mile from the house. And you had a 5000 foot spool of #12/2UF. 5000 feet out and 5000 feet back (2 wires to complete the circuit) is 10,000 feet. There would be 16.19 ohms of resistance in this circuit. Suppose you used a 120 watt lamp. 120 watts at 120 volts = 1 amp. In this case you'd lose 16 volts in the wire itself, leaving 104 volts for the lamp. (Which would now be less than 120 watts, but lets not get too technical!) This would actually work, you likely wouldn't notice the dimming of the lamp.

Now, lets say you got more chickens, and you took a saw out there to add on the building. Lets sat the saw draws 10 amps. We won't consider starting current. At 10 amps we would lose (theoretically) 161 volts in the wire! See a problem?!?? The saw would barely turn, let alone actually cut anything.

Getting back to reality here, #12's are good for 100 to 300 feet, depending on the type of load. It wouldn't bother me a bit to run a heater 300' out, but if there were lights involved, I'd limit it to around 100' or so. You won't notice a heater 'dimming', but lights you certainly would.

Rob

 03-26-2008, 08:06 PM #3 You talking to me?     Join Date: Dec 2007 Location: sw mi Posts: 7,551 Rewards Points: 6,290 here is a jvascript voltage drop calculator. There is no code mandate for voltage drop but there is a recommendation to remain less than 3% in a branch circuit. Use that as a max voltage drop. voltage drop calculator

 03-26-2008, 09:14 PM #4 Member   Join Date: Jul 2007 Posts: 308 Rewards Points: 250 Thanks for the help guys; The voltage drop calculator is really nice. Bookmarked it for future use. FW

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post hsdude1992 Electrical 10 08-19-2015 01:43 PM broken_scout Electrical 26 12-22-2007 10:07 PM diyer4162 Electrical 35 12-20-2007 12:55 PM bonedoc Electrical 9 08-10-2007 09:52 PM wingman Electrical 7 03-05-2006 05:47 PM

Top of Page | View New Posts