Starting in my sub panel, the 50a 220v GFICB white pigtail into neutral bus, black and red legs to line lugs on T104, Green from ground bus in sub to ground pigtail in T104. Then the red and black from the load on the T104 to the Line on the T106, again grounds pigtailed, Then Red and black out of the LOAD on the T106 one to the high speed lug on the pump and the other to the low speed lug on the pump
QUESTON: Both my Pump and mY GFCIB have a terminal for a White/Common, does this go directly to the White/common lug on my pump? As there appears to be no connections for this wire in the timer boxes
Last edited by Al the Diy guy; 02-07-2008 at 09:22 AM.
Do you have 3 wires or four wires to feed the timers.
240 Volt Single Phase:
Black to terminal 1
White to terminal 3
Bare to ground screw in timer.
Term 2 & Term 4 output to motor + Ground
If you have four wires just drop the white as you do not need a neutral for either timer at 240 volts. Your links show both timers to be exact and rated for 208-240 volt.
If the pump motors are 120 volt you can use the timer as a single pole switch. Running the neutral unbroken to the motors. Or you can run the neutral through the switch if you prefer. Just like the 240 volt.