Well pressure switch and outlet
The 120 volt receptacle should be immediately disconnected. Remove both all hot wires from the gold side and all wires from the silver side. A ground wire may remain connected to the green screw. Using ground (equipment grounding conductor) as a neutral was improper as far back as I can remember.
The new 120 volt feed for a receptacle should not come into the existing box with the 240 volt feed. Have a new box for the 120 volt receptacle. Technically you may not have multiple feeds for 120 volts and/or 240 volts coming into the same outbuilding, if you have a separate well house where the well and water softener are located.
The disadvantages of crab apple trees. In summer, the apples are too sour to pick and eat. In winter the birds come and leave dropping all over the place.
Last edited by AllanJ; 10-09-2012 at 09:18 AM.