>>> It is easier to pull one from the closest receptacle, or whatever, than to pull a new wire all the way back to the panel in a finished place.
1. You could pull both hot and neutral from the receptacle and connect that to the portion of the circuit in question after making sure both the original hot and its accompanying inoperative neutral have been disconnected.
2. You might double check all the receptacles etc. on the original daisy chain feed to see if you can find the problem with the neutral. Notably convert push-in-and-stick connections (backstab connections) to screwed on connections.
(One morning on WRKO Radio) The tub's not clean! Let's remodel the bathroom.
(One afternoon on WRKO Radio) It's time for an oil change. I'm going to trade in the car for next year's model.