


Thread Tools  Search this Thread  Display Modes 
10162007, 05:55 PM  #1 
Member
Join Date: May 2007
Posts: 56

Wattage vs. wire size
Is there a formula for this? as based on 120v system.

10162007, 06:01 PM  #2 
Electrical Contractor
Join Date: Jun 2004
Location: Newnan GA
Posts: 5,695

Wattage vs. wire size
P=I*E
Where P=power in watts I=amps E=volts Code states. 14 awg=15amps max 12 awg=20 amps max 10 awg=30 amps max
__________________
Yes I am a Pirate, 200 years too late. "Jimmy Buffett" Last edited by jbfan; 10162007 at 06:04 PM. Reason: add more info 
10162007, 06:12 PM  #3 
Member
Join Date: May 2007
Posts: 56

Wattage vs. wire size
First, thanks for the reply.
So, If I have this right, then the max. wattage for a 120v, with #12 is: Watts(X)=20*120 X= 2400 is this correct? 
10162007, 06:14 PM  #4 
Electrical Contractor
Join Date: Jun 2004
Location: Newnan GA
Posts: 5,695

Wattage vs. wire size
Yep! More letters to make the post long enough!!!
__________________
Yes I am a Pirate, 200 years too late. "Jimmy Buffett" 
10162007, 06:19 PM  #5 
Electrician philosopher
Join Date: Aug 2007
Location: Lilburn, GA
Posts: 838

Wattage vs. wire size
Just for fun, lets say I wanted to put 28 recessed cans in my big pimp kitchen and I was going to use 65 watt bulbs.
I=p/e or (28x65)/120 or i=15.17Amps In this case I would have to use 12 AWG CU wire. Or... lets say I had a 8000watt (or 8kw) heater that operated on 240Volts. I=p/e or 8000/240 or I=33.3Amps In this case I would have to use 8 AWG CU wire. Ohms law is extremely cool even for DIYers to wow your friends at cocktail parties with your knowledge of electrical theory! p=watts e=volts i=amps r=resistance If the electrician knows any two of these he/she can solve for the rest. And I was the kid in the eighth grade bi###ing about the fact that i'm never gonna need this algebra crap EVER! 
10162007, 06:21 PM  #6 
Member
Join Date: May 2007
Posts: 56

Wattage vs. wire size
Thankyou there, jbfan.

10162007, 06:22 PM  #7 
Electrical Contractor
Join Date: Jun 2004
Location: Newnan GA
Posts: 5,695

Wattage vs. wire size
If the electrician knows any two of these he/she can solve for the rest. And I was the kid in the eighth grade bi###ing about the fact that i'm never gonna need this algebra crap EVER!
And I thought that was me!!!! Andy, When you taking the test?(Sorta of topic)
__________________
Yes I am a Pirate, 200 years too late. "Jimmy Buffett" 
10162007, 06:29 PM  #8 
Electrician philosopher
Join Date: Aug 2007
Location: Lilburn, GA
Posts: 838

Wattage vs. wire size
I've got 7 years resi., one year comm. and I'll sit for the GA test in fall of 08 before GA adopts the 08 code. Thanks for asking! I've become a huge code geek just in the last 18 mos.

10162007, 06:33 PM  #9 
Electrical Contractor
Join Date: Jun 2004
Location: Newnan GA
Posts: 5,695

Wattage vs. wire size
I took mine in 96 in at the Gwinnett civic center.
Good luck.
__________________
Yes I am a Pirate, 200 years too late. "Jimmy Buffett" 
10162007, 10:30 PM  #10  
Once fried, twice shy.
Join Date: Sep 2007
Location: Thailand
Posts: 251

Wattage vs. wire sizeQuote:
P(kW) = E(v) x I x Cos phi (this is for single phase power). I = P divided by (E x Cos phi) = 8 000 divided by (240 x 0.8) = 8 000 divided by 192 = 41.7 Amps. When calculating power consumption of equipment, the Power Factor must be considered if the equipment is inductive or capacitive. This formula, P = E x I, is for finding single phase Apparent Power (VA). The formulae for finding True Power (kW) is; P = E x I x Cos phi (single phase). P = 1.732 x E x I x Cos phi (3 phase).
__________________
Switchboard design engineer & Licensed Electrician (Australia). 

10172007, 01:48 PM  #11 
Electrician philosopher
Join Date: Aug 2007
Location: Lilburn, GA
Posts: 838

Wattage vs. wire size
You are totally correct.

Thread Tools  Search this Thread 
Display Modes  


Similar Threads  
Thread  Thread Starter  Forum  Replies  Last Post 
Wire size for distance Question  fburke  Electrical  4  07282007 09:29 AM 
Wire Size Help400ft line to pond for fountain  brownie47854  Electrical  14  04222007 12:50 PM 
Old house, new light fixture, too many wires  Persephonee  Electrical  3  01152007 08:58 AM 
Wire size for Central Air  mwtuck  HVAC  2  12012006 05:06 PM 
wire size wire to 10kw furnace?  lochcarron  Electrical  1  04102005 07:43 PM 