Wattage vs. wire size
Is there a formula for this? as based on 120v system.

P=I*E
Where P=power in watts I=amps E=volts Code states. 14 awg=15amps max 12 awg=20 amps max 10 awg=30 amps max 
First, thanks for the reply.
So, If I have this right, then the max. wattage for a 120v, with #12 is: Watts(X)=20*120 X= 2400 is this correct? 
Yep! More letters to make the post long enough!!!

Ohms law
Just for fun, lets say I wanted to put 28 recessed cans in my big pimp kitchen and I was going to use 65 watt bulbs.
I=p/e or (28x65)/120 or i=15.17Amps In this case I would have to use 12 AWG CU wire. Or... lets say I had a 8000watt (or 8kw) heater that operated on 240Volts. I=p/e or 8000/240 or I=33.3Amps In this case I would have to use 8 AWG CU wire.:thumbup: Ohms law is extremely cool even for DIYers to wow your friends at cocktail parties with your knowledge of electrical theory!:whistling2: p=watts e=volts i=amps r=resistance If the electrician knows any two of these he/she can solve for the rest. And I was the kid in the eighth grade bi###ing about the fact that i'm never gonna need this algebra crap EVER!:laughing: 
Thankyou there, jbfan.

If the electrician knows any two of these he/she can solve for the rest. And I was the kid in the eighth grade bi###ing about the fact that i'm never gonna need this algebra crap EVER!
And I thought that was me!!!! Andy, When you taking the test?(Sorta of topic) 
I've got 7 years resi., one year comm. and I'll sit for the GA test in fall of 08 before GA adopts the 08 code. Thanks for asking!:wink: I've become a huge code geek just in the last 18 mos.

I took mine in 96 in at the Gwinnett civic center.
Good luck. 
Quote:
P(kW) = E(v) x I x Cos phi (this is for single phase power). I = P divided by (E x Cos phi) = 8 000 divided by (240 x 0.8) = 8 000 divided by 192 = 41.7 Amps. When calculating power consumption of equipment, the Power Factor must be considered if the equipment is inductive or capacitive. This formula, P = E x I, is for finding single phase Apparent Power (VA). The formulae for finding True Power (kW) is; P = E x I x Cos phi (single phase). P = 1.732 x E x I x Cos phi (3 phase). 
You are totally correct.:thumbsup:

Andy's heater had a pf of 1.0.......:tt2:

All times are GMT 5. The time now is 12:09 PM. 
User Alert System provided by
Advanced User Tagging (Pro) 
vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.