- - Voltage Drop
||01-16-2007 02:02 PM
I want to install three motion sensor activated flood lights outside. Total amperape for all three lights is 5 amps (non continous...also...assumming I use 6 100 watt bulbs). I plan on tapping in where the garage lights are. The garage lights are on the circuit with one of the 2 15 amp branch circuits servicing the living room. The total run for the three lights on a #14 cable run is 65 feet. Is the potential voltage drop going to be too great? I was thinking about maybe putting the lights on their own 15 amp circuit? Or, maybe running #12 throughout. Will #14 do? Thanks.
||01-16-2007 05:20 PM
The 14 wire will be fine.
|All times are GMT -5. The time now is 01:28 PM.
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved