Voltage Drop - Electrical - Page 2 - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum voltage drop
 User Name Remember Me? Password
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

 Thread Tools Display Modes
04-13-2011, 11:36 AM   #16
Member

Join Date: Nov 2007
Location: Nashua, NH, USA
Posts: 7,971
Rewards Points: 1,548

Quote:
 Originally Posted by Joe Willie Allan, Thanks. Are you referring to 2x6 gauge hots at 3.5v each?
Yes.

A 120 volt 40 amp flow all by itself will experience 3.5 volts drop each way over the wires.

A 240 volt 40 amp flow will experience 3.5 volts drop each way over the wires.

Two current flows of 120 volts and 40 amps each, on opposite sides of the line, will each experience 3.5 volts of drop one way and zero volts drop the other way. This is because (if you think of it that way) the return currents sharing the neutral cancel each other out producing zero amps and therefore zero volts dropped on that leg of the journey.

### Advertisement

__________________
The good conscientious technician or serviceperson will carry extra oils and lubricants in case the new pump did not come with oil or the oil was accidentally spilled, so the service call can be completed without an extra visit.

Last edited by AllanJ; 04-13-2011 at 11:38 AM.

 04-13-2011, 12:43 PM #17 Member   Join Date: Dec 2010 Location: Pass Christian, MS Posts: 66 Rewards Points: 75 OK. You are a good teacher. Another question: If the relationship between voltage and amperage is such, I need at least 10-12 amps to crank the fridge while running an additional 300-400 watts for lights. Given a 20A circuit, 120v, 220' how far above 5% vd would you go?
04-13-2011, 04:55 PM   #18
Lic Elect/Inspector/CPO

Join Date: Apr 2011
Location: NJ
Posts: 369
Rewards Points: 250

Electrical Code book table 310.16

#6 thwn rated at 75 amp 75X 80% is a 60A breaker

use a # 10 insulated ground in the conduit also

### Advertisement

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post Moose50000 Electrical 2 02-28-2010 06:23 PM naehring2000 Electrical 5 02-10-2010 11:14 AM rnice Electrical 8 12-13-2009 08:43 PM rgsgww Electrical 12 12-09-2008 05:21 PM sushiboy Electrical 12 04-03-2008 09:01 PM

Top of Page | View New Posts

 Terms of Use

Search Engine Friendly URLs by vBSEO 3.6.1