Using Additional Ground Bar
I have a 200Amp 40-breaker panel as my main. There is a currently unused additional ground bar that came with the panel. It is bonded to the panel. Do I need to add a wire from the ground bar to one of the neutral/ground bars? Or does the bonding to the panel suffice?
Panel bond is good.
|All times are GMT -5. The time now is 08:35 AM.|
Copyright © 2003-2014 Escalate Media LP. All Rights Reserved