Use well 60A 230V as two 30A 115 outlets?
No. 6 copper wires will barely provide the full 60 amps at 100 feet. You can have the 60 amp. breaker but you will experience noticeable voltage drop when you draw the full 60 amps.
Yes, run the wires to a box (subpanel) where you have 15 amp or 20 amp breakers for your lights and receptacles, and a double breaker for the pump.
(They also make 30 amp receptacles, typically push-in-and-twist type plugs, for which you can have a dedicated 30 amp 115 volt circuit)
The disadvantages of crab apple trees. In summer, the apples are too sour to pick and eat. In winter the birds come and leave dropping all over the place.
Last edited by AllanJ; 11-16-2010 at 07:04 AM.