I have a pretty simple (stupid) question regarding under-tile heating cable for a bathroom.
The install instructions that I was reading in the store stated that the heating cable (mat) needs to have a deadicated circuit.?? What is this??
I have one deplex recepticle in the shower room which is located on other wall so the 1m rule should not apply or do I still need to install a GFCI?
How does one make this (deplex recepticle) a deadicated circuit for the install of under-tile cable heating (mat) for this small room.
I live in Ontario Canada so the OEC rules will apply. Any help would be great. My e-mail is email@example.com
thank you in advance for your help.