Two Sets Of 3 Way Switches On One Circuit. - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Two sets of 3 way switches on one circuit.
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

09-20-2011, 04:32 PM   #1
Newbie

Join Date: Sep 2011
Posts: 1
Rewards Points: 10

## Two sets of 3 way switches on one circuit.

Hello,

My name is Aron and I am in the process of finishing my basement. I am currently working on the electrical and I have a question regarding the wiring configuration for wiring two sets of three way switches.

Here is the scenario. I am running 12ga wire throughout to 20A circuits. The living room is approximately 17ft wide by 28ft long and the wife bless her soul, has her heart set on 15 can lights.

So I was thinking a three way switch to work them all. One on each end of the room. I could do that, I have a wiring book and am fairly confident. The wrench in my plan is she wants three rows of the lights to work with one set of switches and the remaining two to work with the other. My first thought was to run the configuration I am comfortable with to two different circuits, but I believe this will be wasteful and Arc fault breakers for future bedrooms are going to eat up my available space.

So…

Can someone help me with how I would make mama happy and only use up one circuit. I have plenty of 12-3 and 12-2 wire.

09-20-2011, 05:17 PM   #2
Member

Join Date: May 2009
Location: Easton MD
Posts: 1,893
Rewards Points: 1,104

1 Power 12/2 to first set of switches. 2 12/3 cables to other set of switches. 1 12/2 to each set of lights.

 09-21-2011, 07:34 AM #3 Newbie   Join Date: Sep 2011 Posts: 2 Rewards Points: 10 think you have that backwards. Power is coming through the switch and then into 9 lights. I assume the next three lights are on the next switch. With this setup, you have to turn on the 9 lights just to turn on the 3 lights. Correct? 14-2 will do just fine, you only need a few inches of wire to make the necessary pigtails in the J-box. Electricians Melbourne CBD
 09-21-2011, 10:24 AM #4 Member     Join Date: Mar 2005 Location: Welland, Ontario Posts: 12,362 Rewards Points: 11,516 Blog Entries: 11 It is as simple as creating two switch setups and using the same power source. There is no need use two circuits for these lights. If you can wire up one all the light then simply wire up six of them with that setup and then copy it for the other three. Use the same p ower source for both of them by pigtailing two black wires to the incoming power for connection the the two switches.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post RyanS2000 Electrical 4 09-11-2011 04:21 PM tertius Electrical 9 09-24-2009 09:17 PM BeginnerHomeDIY Electrical 7 07-08-2009 03:40 PM DrP Electrical 8 05-25-2006 11:05 PM Unregistered Electrical 1 03-07-2004 04:39 PM

Top of Page | View New Posts