With wiring that old and by the questions your asking you really need to call a real electrition to come look this over and do it for you.
Something that old will need all new wires from the pole, new panel and all new wires.
The Following User Says Thank You to joecaption For This Useful Post:
You need a disconnect as close as possible to where the power feed cable enters the house. 75' away is too far. You need a disconnect. You can get a meter pan with a disconnect in it. Then you won't need the disconnect inside.
Do not PM with questions that can be asked in a forum. I will not respond.
The Following 2 Users Say Thank You to joed For This Useful Post: