might have answered my own question but,
The Ground bar can either by the same or separate from the Neutral Bar? so its more for organization purposes from what i under stand?
As far as the conduit goes, correct me if im wrong:
-Copper, for ground
-White, for Netural
-Black/Red, for the HOT incoming wires?
So, if I buy 120/240v receptacle like this
will I be in business?
For attaching my conduit to the Switch pannel itself;
-Red/Black wires go into the Terminals on the breaker
-White goes to the Neutral Bar in front
-Copper Goes to the small Ground in the back.